What separator size do I need?
Answer: Flow rate is the most important factor in determining separator size because all LAKOS Separators operate within a prescribed flow range. Pipe size is not a factor in model selection so do not use your existing pipe size to determine the separator size. Required separator size is often, but not always, smaller than the existing piping, and appropriate hardware is used to match the inlet/outlet size with existing piping.
What is the factory timer setting of the Auto Purge Controller?
Answer: LAKOS factory-built purge controllers (ABV, ABV2, AKE, APP, AFS, EFS) do not have factory-set timings. The required purge frequency and durations vary depending on flow rates, solids concentrations, type of solids, etc. The controller time settings must be set at installation and LAKOS literature LS-608 can be used to help establish purge duration and frequency based on the application.
How long do I purge?
Answer: To determine the necessary purge frequency, purge often at first and calculate the proper rate based on the expected volume of separated solids. Purge duration should be long enough to evacuate the purge chamber AND clear the entire length of the purge piping of all solids. This is usually indicated by a change in the color of the purged liquid from dark to light. The time between purges should never exceed the time it takes to fill 1/3 of the collection chamber volume, based on the expected solids load and the separator's purge collection volume, as indicated in the separator's literature. Refer to LS-608 for additional information on calculating purge frequency and duration.
How long will the separator last?
Answer: While there are many LAKOS Separators still in service after 15-25 years, there are many variables to the longevity of a LAKOS Separator. It can generally be expected to last as long as any other materials of similar construction in that system. Environment, fluid chemical make-up, flow, material of construction, type of solids, and maintenance purging are all important factors to the life of a separator. It is important to take all these factors into consideration when purchasing a separator. Providing LAKOS with details about your application will insure your separator meets or exceeds the life expected through your purchase. Consult your LAKOS factory representative to obtain the life expectancy in your specific application.
What size media do I need in a sand media filter (All models)?
Answer: Media filtration sand requirements are based on
the filter's downstream equipment needs. In the case of
micro-irrigation system protection, the minimum orifice diameter of the
devices (emitters, drip tape, etc.) will generally dictate the
filtration level required. Once this orfice size has been determined,
the following guidelines will be helpful:
Sand media used Filtration levels
#20 Filter Sand 200 - 250 mesh (74-63 microns)
#16 Filter Sand 150 - 200 mesh (105-74 microns)
#12 Filter Sand 120 - 150 mesh (125-105 microns)
Using media sand finer than required will cause slightly higher system pressure losses, and more frequent backwashing, so only use what is actually required to protect your downstream equipment.
What is the efficiency of the separator?
Answer: Solids-removal efficiency is affected by a
number of factors, including the difference in specific gravity between
the solids and the carrying liquid, the viscosity of the liquid, the
particle shape, and any purging enhancement techniques. In general,
with a specific gravity ratio of 2.6 (e.g. quartz sand in fresh water),
liquids of 31 SSU viscosity, and generally round particles, a single
pass through a separator predictably removes 98% of particles 74 microns
(0.0029 inches) and larger. Appreciable quantities of particles finer
than 74 microns are also removed, as well as particles of lighter
specific gravity. Higher specific gravities (like mill scale in water,
where SG=5.7) result in much finer levels of filtration.
Recirculating systems (running the fluid through one or more separators continuously) can also result in appreciable removal of particles down as fine as 5 microns.
Contact LAKOS for assistance determining performance expectations on your specific application.
How do I determine what I need for basin sweeping in HVAC systems?
Answer: As a rule of thumb, LAKOS uses a sizing factor
of 1 GPM per square foot of basin area to determine the required size of
a Tower Clean (TC) system. Using this factor, multiply the square
footage of the cooling tower basin (L x W) by 1 GPM / sq. ft. This gives
the basic flow rate for sizing the TC system. Tower Clean literature
LS-710 can also be used as a reference for more information and
For industrial applications or very heavy solids loadings, consult LAKOS for recommended basin sweeping flow rates.
What material of construction is available for a separator?
Answer: As a standard, most separators are available in mild carbon steel and 304L/316L-series stainless steels. Specially designed separators can also be constructed in most weldable metals, including, but not limited to: super duplex stainless steels, chrome-moly, titanium, Hastelloys, nickel alloys, and cupronickel. In special cases, separators can also be fabricated in plastic or fiberglass. For materials other than carbon and stainless steel, consult with LAKOS on the availablility of your specific material requirements.
Separator or sand filter?
Answer: LAKOS separators and sand filters are both
designed to remove solids from liquids, but have advantages over each
other depending on the application.
A separator is designed to remove solids with a specific gravity at least 1.5 times that of the carrying liquid. Separators require very little, if any, maintenance because they have no moving parts. The pressure loss across a separator is predictable and steady, and only varies with flow rate. Separators require minimum liquid loss for purging of collected solids, and can also be equipped with an optional solids recovery vessel that can eliminate liquid loss. However, separators do not generally help with liquid clarity (turbidity) and are ineffective on organic material, such as algae.
A sand media filter is designed to remove finer solids (down to 5 microns in size) with low specific gravities. Sand filters are used when finer filtration and liquid clarity (turbidity reduction) are a requirement. Sand filters do require more operational maintenance (more moving parts), and use more liquid for backwashing of the sand bed to remove the collected solids. Pressure loss across a media filter varies, as solids are collected and enter a backwash cycle when they reach a predetermined pressure loss. However, sand media filters are very efficient at removing a wide variety of light, organic solids.
What is the greatest solids load the separator can handle?
Answer: The maximum solids loading on LAKOS Separators is recommended to be less than 1% by volume. While 1% may seem low, keep in mind that 1% in a small 100 gpm system is 1 gallon of solids every minute, or 1,440 gallons (twenty-six 55-gallon drums) of solids per day. Models H20, SMP, and MAX Separators for residential use are not recommended to exceed 0.25% by volume. ILB Series Separators are not recommended to exceed 0.50% by volume. If your application exceeds these limitations, please consult your factory representative for proven alternatives.
Will the separator work on fluid other than water?
Answer: The LAKOS Separator is capable of working with any liquid that has a viscosity less than 100 SSU. The solids to be separated must also have a specific gravity at least 1.5 greater than the fluid. The greater the specific gravity of the separable solids and the lower the viscosity of the liquid, the better the LAKOS Separator will work. A good rule of thumb: if the solids settle within 3-4 minutes in your liquid, they will likely be separable with a LAKOS Separator.
What is the maximum temperature?
Answer: Standard maximum temperature rating for operating most LAKOS Separators is 180°F. The exceptions are the H20 and SMP Separators, which have a maximum temperature of 120°F, and the MAX Separator, which has a maximum temperature of 125°F. LAKOS can easily accommodate higher temperatures with custom separators.
What is the maximum pressure?
Answer: Standard maximum pressure rating for most LAKOS Separator is 150 psi. The exceptions are the H2O, SMP, and MAX Separators, which have a maximum pressure rating of 100 psi. Contact the factory for higher pressures; LAKOS can accommodate pressures up to 3000 psi through custom separators.
Can you do CRN?
Answer: Yes, we can manufacturer a separator with a Canadian Registration Number (CRN). We must know the Province or Territory the vessel is to be located so we can contact the registration controlling agency within that Province or Territory to determine the cost and lead time.
Where does the sand go when operating a Pump Protection Separator (PPS)?
Answer: The sand goes to the bottom of the well. Over time, the flow dynamics of the well formation are changed due to the accumulation of the sand, and water is pumped without disruption through the life of the well. In fact, in over 30 years of experience with PPS Separators, less than a handful of wells have ever needed to be bailed, and in those few cases, the benefits received from longer, more efficient pump life far outweighed the one bailing.
How often should I backwash a sand media filter?
Answer: It is recommended that backwashing should take place at an interval when it is anticipated the filter system will have a 7 psi pressure drop. This 7 psi differential is in addition to the normal operating pressure drop when the filter is clean. If the filter media does not achieve this differential over a 24 hour period, it is recommended that the filter be backwashed once a day as a minimum.